Most people asked us: How to calculate the tonnage or HP (horsepower) untuk Penyaman Udara equipment and Bilik sejuk sistem penyejukan? Baiklah, actually there are many aspects can affect the cooling performance of refrigeration equipment, cooling capacity is the most important one. As our 12+ years experience, believe we can provide the most suitable solution for your project.
Notis: Cooling performance will be affacted by many other factors: room set temp, ambient temp, kelembapan, pengudaraan, installation height, dan lain-lain. So please tell us more details about your project, we will give you the most suitable solution. For more request, please contact us freely.
soalan: How to calculate which HP(horsepower) sistem penyejukan ( condensing unit or unit cooler) should need for my cold room?
Jawab: Baiklah, 1) calculate your room dimension: Length*Width*Height, 2) divided by coefficient.
Low set temp (<-20°C): Volume/11
High and medium set temp(>-15°C): Volume/14
1) Cold room size: 6*6*3m, room set temp -20°C
So you need Refrigeration HP= 108m3 / 11 = 9.8 ≈ 10hp
2) Cold room size: 6*6*3m, room set temp -5°C
So you need Refrigeration HP= 108m3 / 15 = 7.2 ≈ 7hp
Panel bilik sejuk is the essential component for cold room, but many people don’t know how to calculate the whole panel area for a cold room? Pertama, you should calculate all the 6 sides of the cold room: roof + dinding + floor. Kedua, you should know the set temperature for the cold room, because different set temp use different thickness panel (means different price):
|Ketebalan Panel||Panel Material||Sambungan Panel||Cold Room Set Temp|
|75mm||PU/PIR||Camlock / Slip Joint||>0°C|
|100mm||PU/PIR||Camlock / Slip Joint||0 ~ -15°C|
|150mm||PU/PIR||Camlock / Slip Joint||-15 ~ -35°C|
|200mm||PU/PIR||Camlock / Slip Joint||<-35°C|
Perhatian: Panel cost will vary due to the raw materials’ cost changing. So before you calculate the total cost for your cold room project, please contact us to verify the newest unit price.